CAN ULC S536 PDF
CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Published (Last):||24 December 2015|
|PDF File Size:||7.86 Mb|
|ePub File Size:||3.2 Mb|
|Price:||Free* [*Free Regsitration Required]|
Backflow prevention assemblies have been tested by an agency acceptable to the local authority? Gauges checked against calibrated gauge or replaced? No Summary Work Order Cab C Tested and confirmed operation of alarm relay.
Fire Alarm System Periodic Inspection (CAN/ULC-S)
Refer to Appendix F1 ; P iii Silent accelerated test. Automatic transfer from alert to alarm signal cancel acknowledge operates on a two stage system. Sprinklers and spray nozzles protecting commercial cooking equipment and ventilating systems replaced except for bulbtype which show no sign of grease buildup?
Individual alarm and supervisory zone indication operates. Cooling water level is normal Inspect exhaust hangers and supports? Status change confirmation inspected and tested.
Test batteries for specific gravity and state of charge? Two stage pull stations tested and functions confirmed? Battery Type as installed: Where active and supporting field devices are utilized, device labels correspond with actual field location.
These sensors have a limited service life usually ten years and some require regular battery replacement. Failure to flush yard piping or surrounding public mains following new installation or repairs? The audible signals can consist of bells or buzzers, but in some systems, an alarm tone is generated through a series of speakers located on each floor of the premise. Yes Last Service Date: System in service on inspection?
Gauges to ensure good condition and normal pressure?
Smoke control installed in accordance with Measure: We provide expert inspection services to all makes and models of fire alarm and extinguishment systems. The printed maintenance and testing guide must be followed. Forward Flow Test results are recorded on ulf backflow test report?
Combination appliances individually inspected and tested. Advise fire department that testing is completed? Manual Pull stations tested? Battery Capacity as installed: There are a number of companies in the Lower Mainland that uoc this service.
Building Life Safety Audits. Actual Time to Test Building: Minor leak at no flow?
Pressure control valve passed test? Obstructive material discharged during water flow tests?
Fire Alarm System Inspection Services. There are a total of: T Generator provides power to the AC circuit serving the fire alarm system. Interior of dry-pipecn, deluge valves internal inspection? Photoelectric type smoke detectors utilize an infrared light source called the emitter and a receiver, both of which are located inside the sensing chamber.
In-suite signal isolator modules have been identified, individually inspected, and tested.
Engine hour clock reading: U Output circuit supervision fault e536 a trouble indication. Yes No Last Service Date: The fire signal receiving centre transmitter is located remotely from the fire alarm control B unit. Extinguishment, Deluge, and Sprinkler Systems.
Standards Council of Canada
Date of service from records on site was: Monthly Inspection and Tests A Pilot lights are functioning? Batteries 2 charging current is normal Check pump coupling alignment? Sprinkler System Testing Continued: Multi-line sequential display operates as per Appendix C5.
AH R Record the battery terminal voltage after tests are completed.